CellarPro Air Handler Split AH8500Si-ECC Indoor #36020
7156 SENSIBLE BTUH @ 55F.
CellarPro’s AH8500Si-ECC ducted cooling units (1 Ton Nominal) are engineered for wine cellars up to 2,500* cubic feet in both commercial and residential wine cellars. When ducted, this unit uses 10-inch insulated ducting on the cold side, and 10-inch ducting on the hot side.
This unit maintains optimal cellar temperature and humidity conditions in extreme conditions up to 110F. AH8500Si units use energy-efficient EC fans and are significantly quieter than comparable units from other brands. Visit our Learning Center for data tables, performance charts and product comparisons among different brands.
When the condensing unit will be exposed to or pulling air that is below 40F, our Compressor Heater (P/N 1727) is a required addition to protect the compressor. For installation of the condensing unit in environments below 20F down to -20F, our Fan Cycling Switch (P/N 6972) is required in addition to the Compressor Heater, and Electronic Configuration is required.
*Assuming R19 insulation throughout the cellar, 55F inside the cellar and 85F outside the cellar. Cold-side ducting, glass and/or uninsulated walls, extreme humidity, altitude and other factors may affect the sizing calculation.
Our cooling units are designed to be used in properly-constructed wine cellars that are adequately insulated, airtight and sealed with a vapor barrier. In improperly-constructed cellars, the cooling unit will create excess condensation, leading to damage and premature failure of your cooling unit (not covered by warranty).
- CellarPro AH8500Si-ECC units are designed to be ducted, with the evaporator near (or inside) the cellar, and the condensing unit in a remote interior location up to 100 feet away.
- The evaporator and the condensing unit each can be ducted up to 100 Equivalent Feet (50 Feet per Duct) with 10-inch ducting .
- CellarPro’s split configuration allows multiple ducting alternatives, as follows.
- Collars or grills for EXHAUST (ie Supply) are located at the front (shown at left), top or rear of the cooling system, and are interchangeable to meet your specific requirement.
- Collars or grills for INTAKE (ie Return) are located at each end (left: evaporator, and right: condenser), and include professional-grade air filters to protect the unit.
- We recommend pulling the fresh air intake (hot-side) from a temperature-controlled environment other than the cellar. If the hot-side exhaust will be directed to a different space than the intake, always make sure that both spaces are sufficiently voluminous so that you don’t run into issues with negative pressure.
- A bottle probe temperature sensor (10′ cord) plus your choice of duct collars, indoor grills and blank plates are included in the price of the cooling system.
- CellarPro Air Handler Split systems offer a choice of 110V / 60Hz wiring and power configurations:
- Two permanent power connections for the evaporator (2.0 amps / 15 amp circuit breaker) and the condensing unit (15.7 amps / 25 amp circuit breaker). This wiring configuration is recommended for Valve Control.
- One permanent power connection for the entire system (25 amp circuit breaker). In this configuration, the condensing unit must be wired to the evaporator, and must be used with Electronic Control.
- The amp data above is not valid when the integrated heater and/or humidifier are configured with the cooling unit – please consult those Owner’s Manuals for the additional amps required when using those upgrades.
- When the control panel is difficult to access, we offer a remote control display kit which is wired to the cooling unit and allows the digital display to be mounted inside or outside the cellar.
- The condensing unit requires 12 inches of unobstructed space in front of the coils, and requires approx. 600-700 CFM of ventilation when installed in a confined space.
- For installations in environments below 40F, AH8500Si-ECC units require our Compressor Heater (P/N 1727) .
- For installation in environments below 20F down to -20F , Electronic Control is the required configuration, and our Fan-Cycling Switch (P/N 6972) is required in addition to the compressor heater (both sold separately).
- The evaporator should never be exposed to temperatures below 32F.
- Access to the left and right side of the evaporator unit is required for installation.
- All split systems must be installed and charged on site by a qualified HVAC professional. Line-set equivalent feet must be calculated in accordance with ASHRAE guidelines; refer to our Line Sizing Chart for more information.
- A CellarPro cooling unit must always be used in the upright position, and should never be operated on its side or upside down.
- We ship these units strapped to a pallet via common carrier with curbside delivery. Inside delivery is available for an additional charge.
- Cold Temperature
- Compressor Heater #1727: protects the unit when installed in environments that drop below 40F down to 20F
- Fan Cycling Switch #6972: supports the unit in temperatures below 20F and as low as -20F when configured with Electronic Control and combined with our compressor heater.
Filters & Grills
- Use our filter & grill guide to find the cooling unit filter or duct filter and/or duct grill that is appropriate for your cooling unit.
Remote Thermostats, Displays & Probes
- Networkable Thermostats #27346 and #27310: connect your cooling unit to a networkable, wi-fi enabled thermostat (sold separately). Must be ordered at the same time that the equipment is ordered. Other limitations apply – read the networkable thermostat description for more information. Includes 10 feet of wiring.
- Remote Display #1603: lets you place the digital panel wherever you want, whether inside or outside the cellar. Includes 10 feet of wiring. Additional wiring is available at a cost of $0.50 per additional foot.
- Bottle Probe #1434: this remote thermostat with a 10-foot cord overrides the thermostat on the face of the cooling unit, and allows it to monitor air or liquid temperatures at various locations inside the cellar – included.
- Bottle probe extension cords are available in 25-foot (#1780) and 50-foot (#1781) lengths.
Heating & Humidification
- Integrated Heater 900W #7237: adds 900 watts of heat through the cooling system when the cellar is in an unheated environment and will be exposed to temperatures below desired wine storage temperatures.
- Integrated Humidifier #7236: provides humidification with digital control inside the cellar when attached to an external water line.
- Capacity:7156 BTUH @ 55F
- Sizing:Click here to view sizing table
- Size:18 3/5w x 18 3/5d x 19 3/10h (in) (Evap) 10-Inch Ducting
- Weight:226 lb
– CellarPro Air Handler Split systems offer a choice of 110V / 60Hz wiring and power configurations:
- Two permanent power connections for the evaporator (3.5 amps / 15 amp circuit breaker) and the condensing unit (15.7 amps / 25 amp circuit breaker). This wiring is recommended for Valve Control configurations.
– Startup Amps: 54.5 Amps
– Running Amps Cord-Connected: 15.7 Amps
– Total Watts: 1268 (medium fan speed)
– 1 Ton Nominal
BTUH @ 55F
– Low Fan Speed: 6245
– Med Fan Speed: 6649
– High Fan Speed: 7156
– Low Fan Speed, Ducted: 47 dBA
– Med Fan Speed, Ducted: 51 dBA
– High Fan Speed, Ducted: 59 dBA
Condensing Unit Decibels
– Low Fan Speed, Ducted / Non-Ducted: 45 dBA / 58 dBA
– Med Fan Speed, Ducted / Non-Ducted: 52 dBA / 65 dBA
– High Fan Speed, Ducted / Non-Ducted: 57 dBA / 70 dBA